Make sure the setting matches the installed heating and/or cooling system. Pressure switch opens at 40 psig (system shuts down) and closes at 90 psig (system restarts). Cooling operation is not allowed. You may need to simply press EDIT. Do the following to prevent or reduce the risk of heat pump not defrosting issue: Remove leaves and debris from the outdoor coil. The system will go into Watchguard mode. The system will not use the heat pump to warm your home. Provide power voltage within proper range. As a result, the system has shutdown the outdoor unit. Remove power to thermostat before programming the unit control board. Replace the control if the problem prevents operation and is persistent. (Outdoor Unit) The “W” output on the outdoor unit has reported more than 5 errors. Heat section / Stage 2 failed (Same as Code 351). The thermostat will shut down the system. Defective pilot generator (thermocouple). Either the pi- lot relay contacts did not close, or the relay coil in the electric heat section did not energize. Check for dirt or debris blocking air flow to outdoor unit. Shut off gas. HP22 Series Units. heat choice on an HP system. The alarm/fault clears after blower demand is satisfied. Check for other alarms/codes that may be preventing the system from operating as expected. Check system charge using approach and sub cooling temperatures. Check thermopile with millivolt meter. acquire the lennox heat pump troubleshooting guide link that we have the funds for here and check out the link. Check for connections to other wireless devices and internet connection. The icomfort does not display an alert code message, but the furnace or unit control displays a diagnostic code. Check the accuracy of the thermostat temperature sensor. Fan does not turn on in a call for heat (electric furnaces only). Voltage sensed on W output terminal when Y1 out is deactivated. • Check the heat temperature setting to be sure it is set above the room temperature and “Heat On” is displayed solidly on the screen. If problem persists, then check all DEVICE connections to make sure they are icomfort-compatible. Check for dirty filters and other air flow restrictions. (Stat) The outside temperature is below the level where the heat pump is programmed to heat the home. Check for a high voltage source of noise close to the system. Heat pump iced-up in Winter: Heat pumps can ice-up during the winter time. Open high pressure switch error count reached 5 strikes. HVAC Troubleshooting Guide-Rex Miller 2009-02-10 A Practical, On-the-Job HVAC Guide Applicable to residential, commercial, and industrial jobs, this essential handbook puts a wealth of real-world information at your fingertips. If pilot lights, turn off pilot and trigger the igniter button again. If 2 stage with float switch, the IFC control R-DS is open. Check all connections and cycle system power. The “W915 2 Stage Compr” clippable option link on the furnace or air handler control must be cut when used with a non-communicating 2-stage outdoor unit. The alarm/fault clears when a heat call finishes successfully. System reset is required to recover. Thermostat will display Settings were copied after successfully copying the information to the new control. The system will go into Watchguard mode. I read this directly from an un-named article on the internet that has a number one position in a search for troubleshooting heat pumps – “check the heat pumps ignition”. Heating system does not turn off and the heat temperature setting is set below the room temperature ("Heat On” is not shown in display.). Critical Alert. Elite Series, Heat Pump, 1.5 Ton, 14 SEER, 1 Stage, R-410A, XP14-018-230 RS Check the Thermostat. If fault persists, then cycle power. Mini-Split Multi-Zone Heat Pumps. Select “Sys- tem" from the device list using the up/down arrows and press the edit button. System resumes normal operation 5 seconds after fault recovered. The alarm is only cleared by pressing the clear button on the Installer Alerts Tab. Lennox Heat Pump Troubleshooting Guide related files: 23e9c2f922597ed15fccb67491aacbfc Powered by TCPDF (www.tcpdf.org) 1 / 1 The alarm stops all associated HVAC operations and waits for a heartbeat message from the unit that's not communicating. That’s why we offer a collection of resources that make it as easy as possible for you to get the answers and support you need. Check and correct voltage. Shut off gas. Thermostat (electronic) clicked on & unit & blower energized. Heating system does not turn off and the heat temperature setting is set below the room temperature (’’Heat On” is not shown in display.). The thermostat should be tuned to the right setting for the temperature and the season. Correct the cause of rollout trip. Cleared after communication is restored. Thermostat is asking for heating or cooling to come on (screen shows -Heat On- or -Cool On- in display) but there is no heating or cooling running. The unit is reporting that its power line and neutral are reversed. Outdoor Temp Display must be enabled to display the outdoor temperature on the home screen. The thermo- stat will not allow any heating operation to begin until it senses a temperature lower than 99°F. (Furnace / Air Handler) The system has lost communication with the (furnace or air-handier) indoor blower motor. Unit control initiates a 3-minute delay at the end of each cycle to protect the compressor from damage. [Indicated uni? Check to see that batteries are properly installed. Follow the red instructions then exit the system. Let’s Not Get Trippy When your heat pump trips your circuit breaker,… - icomfort system is not able to read the outdoor temperature sensor in the icomfort outdoor unit, check outdoor sensor. Make sure the thermostat's Wi-Fi is enabled and connected to the home network (Router). Most heat pump malfunctions relate to … If you don’t have the necessary knowledge and skills, call a heating repair technician (HomeAdvisor).. Heat Pump Doesn’t Heat or Cool Right. Under normal conditions, your heat pump periodically switches to air conditioning mode for a few minutes, which heats up the outdoor coils enough to melt any frost and light ice that has accumulated. Click on Shop Parts, or select the kind of product you're working with on the left and we'll help you find the right part. Replace motor or wheel if assembly does not operate or meet performance standards. Compressor ran more than 18 hours to satisfy a single thermostat demand. (Furnace) The furnace high pressure switch is stuck closed. Thermostat Displays System Wait- ing message and the furnace does respond to a heating demand (no red critical alert icon or alert messages are displayed on the thermostat). (Furnace) The indoor blower motor is over heat- ing. (Furnace) The furnace hot surface igniter is open. Check for 24 Vac between the heat terminal (W) and transformer common. If having difficulty connecting to the router, online research the router model number and/or internet provider to discover and verify that the router band is set to B, G or N bands. Clears the code after voltage is higher than 20 VAC for 2 seconds or after power reset. Inspect vent and combustion air inducer for correct operation and restriction. Unable to perform pressure switch calibration. Set system Selection to correct position. (Air Handler) An air-handier configuration jump- er is missing. (Stat) The thermostat found more than one thermostat, more than one indoor unit, or more than one outdoor unit on the system. (Furnace) The furnace control has switched to high fire ignition because the low fire pressure switch did not close in the allowed time. Make sure coil is clean and airflow unobstructed in and out of condenser. This article is for troubleshooting heat pumps only. (Stat) The thermostat cannot find an icomfortenabled indoor unit. Mea- sure voltage of neutral to ground to ensure good unit ground. [Indicated unif\ is missing the programmed unit capacity. Thermostat is calling for Heat (Heat on) or Cool (Cool on) but no heating or cooling is running. If your heat pump tripped your circuit breaker, be happy. Check connections. 35,400 btu cooling, 11 EER, 13 SEER, 35,400 btu heating at 47F, 7.7 HSPF, 21,600 btu heating at 17F. Compressor minimum-off timer is activated. If above 90 ohms, check and repair wiring, splices or other wiring defects that may be causing the excessive resistance. (Outdoor Unit) The “W” output terminal on the outdoor unit is not wired correctly. (Outdoor Unit) Either the compressor ran for more than 18 hours continuously trying to cool the home or the refrigerant pressure in the sys- tem is low. (Stat) The system has not been able to turn on the heating for more than 45 minutes. Scroll down the menu item choices to Balance Point Control and press edit. (Stat / Furnace / Air Handler / Outdoor Unit) The (stat, furnace, air-handier or outdoor unit) has lost communication with the rest of the system. Step 1: Check all heating equipment to determine cause of heating demand. lennox-heat-pump-troubleshooting-guide 1/1 Downloaded from ehliyetsinavsorulari.co on January 16, 2021 by guest Kindle File Format Lennox Heat Pump Troubleshooting Guide When people should go to the ebook stores, search initiation by shop, shelf by shelf, it is in point of fact problematic. Replace thermostat, if needed. (Stat) The thermostat does not know the capac- ity (tonnage) of the (furnace, air-handier or out- door unit). Backlighting seems dim; is it designed to be dim? - Replacement icomfort controls do not have the Model # or Serial # loaded in the control. The alarm/fault will clear when a heat call ends successfully. Wait up to five minutes for the system to respond. Press the setup tab, press start, and press confirm. Fault clears after communication is restored. Heat pumps come with a built-in defrosting component that allows them to melt off accumulating frost during cold weather. In the thermostat installer program select the setup button and follow the on screen instructions until you reach the Add or Remove Non- communicating equipment screen; press yes. Heat pump problems are often caused by thermostat malfunctions. There is a control hardware problem. This event may occur during a power outage or power fluctuation in the system. Measure the resistance of hot surface igniter. If voltage is not present, check the heating equipment to find the cause of the problem. (Outdoor Unit) The outdoor unit pressure is be- low the required limit. Heat pump running constantly. If the pump is off, it may be due to settings on the control panel. (Furnace / Air Handler) There is a problem with (furnace or air-handier) discharge air sensor. Reconfigure system. Our library is the biggest of these that have literally hundreds of thousands of different products represented. (Furnace) The furnace primary limit switch is open. (Furnace) The reporting device cannot find earth ground. (Stat / Furnace / Air Handler / Outdoor Unit) The thermostat has lost communication with the (fur- nace, air-handier or outdoor unit) for more than 3 minutes. The heat pump condenser and coil are a match. Mini-Split Single Zone Heat Pumps. Check for proper configuring in installation instructions. (Air Handler) The air handler control software is corrupted. • If the problem has not been identified and corrected, contact a qualified service technician. System resumes normal operation 5 seconds after fault recovered. System resumes normal operation 5 seconds after fault recovered. There is a control hardware problem. Recalibrate thermostat to clear; adjust setpoint. Also for: Merit 13hpx-018, Merit 13hpx-024, Merit 13hpx-030, Merit … Thermostat is calling for heat (Heat ON) or cool (Cool ON); but HVAC system is not operating. The sys- tem will go offline for 60 minutes and try again. Check for proper configuring under Configuring Electric Heat Stages in the air handler installation instructions. Measure voltage of neutral to ground to ensure good unit ground. Check filter and duct system. The alarm/fault will clear after the issue is corrected. This event may occur during a power outage or power fluctuation in the system. The alarm/fault is cleared 300 seconds after the fault recovers. Also check to ensure If “Heat On” is shown solidly in the display, but the heating system does not turn on. Check pressure (inches w.c.) of low pressure switch closing during a heat call. To troubleshoot a unit the location of the many sensors will need to be known. (Stat) The thermostat is reading indoor humidity levels above the pre-programmed limit. Allow the system to stabilize and complete the calibration mode due to the time delay. Both heating and cooling systems are operating at the same time. Applicable in non communicating mode. Heat Pump will not be used to service a heating demand. Heat Pump Repair Advice Advisory. I will monitor as I can, Have to go earn money now. Most heat pump malfunctions relate to thermostat, defrost or airflow problems. Typically the control will re-set itself. Inspect vent and combustion air inducer for correct operation and restriction. Turn off the power to the system and correct the line power voltage wiring. Bookmark File PDF Lennox Heat Pump Troubleshooting Guideyou're looking at free books. If persistent or if it coincides with the system operation then proceed with the following steps. - Verify the indoor unit has a icomfort communicating control. Make sure that the heating/cooling setting is set appropriately. (Furnace) There is over current in the furnace inducer motor. (Pilot relay contacts did not close, or the relay coil in the electric heat section did not energize.) Notification only - Outdoor Temp is below the Low Balance Point. If gap does not measure 1/8", replace pilot. (Furnace) The furnace gas valve 2nd stage relay is faulty. Configuration link R to 0 needs to be restored. (Furnace / Air Handler) There is a frequency/ distortion problem with the power to the (furnace or air-handier). (Furnace) The furnace rollout limit switch is open. Check operation of low pressure switch to see if it is stuck closed for longer than 150 seconds during a heat call . The heating equipment is not a heat pump but the System Type (Installer Set- up Number 0170) is set to Heat Pump. Pilot will not stay lit after carefully following the lighting instructions. (Outdoor Unit) Either the discharge or suction pressure level is out-of-limits, or the is compressor overloaded. Check Installer Set-Up Number 170: Heating and/or Cooling Type. (Furnace) The reporting unit has poor earth grounding. I-, C wires for open/shorts. The variable capacity Lennox heat pump premium model means you get a modulating heat pump. System resumes normal operation 5 seconds after fault recovered. Lennox Thermostats Troubleshooting If you experience technical problems with a Lennox thermostat, the guidelines below will help you to solve the issues. If problem persists, then check all DEVICE connections to make sure they are icomfort-compatible. Heating operation is not allowed. To clear, replace filter if needed or repair/add duct. User manuals, Lennox Heat Pump Operating guides and Service manuals. Please program the correct capacity of the (furnace, air-handier or outdoor unit). (Air Handler) There is a problem with the air- handler’s 2nd stage electric heat. MORE key remains blank unless the Furnace Filter Change Reminder has been turned on. Measure resistance of hot surface igniter. A heat pump that will run only at a speed necessary to maintain demand. Check system operating pressures and compare to unit charging charts in installation manual. The alarm/fault will clear when a heat call ends successfully. | Contact. Key to the right of the screen key is blank. Check blower performance. The alarm will clear when 24VAC is continuously sensed on DS terminal for a minimum of 10 seconds or on a power reset. Check the wiring connections, ohm wires and cycle power. (Air Handler) The air handler control software is corrupted. (Outdoor Unit) The compressor ran for less than 3 minutes to satisfy a thermostat demand. Select heating system mode to heat the indoor space to above 40?F. If both switches are in the ON position, it may result in excessive resistance (and millivolt drainage) and the burner may not come on. (Stat) The (furnace, air-handier or outdoor unit) is resetting itself. The sys- tem will go offline for 60 minutes and try again. To get started finding Lennox Heat Pump Troubleshooting Guide , you are right to find our website which has a comprehensive collection of manuals listed. • Wait five minutes for the heating system to respond. The alarm/fault clears after communication is re-established. The alarm/fault will clear when a heat call ends successfully. Go to [Indicated unif\ and program the unit capacity manually. Check for dirty filters. Let the heat pump defrost itself if it’s only covered with thin ice. (Stat) The thermostat is reading an indoor temperature that is lower than 40?F. (Furnace) The furnace flame is out of sequence. After 10 minutes, operation is discontinued. Furnace will operate on 1st stage for the remainder of the heating demand. Manual is applicable only to the following models – LNIV2610, LNIV3510, LNIV5010, LNIV6510. If “Heat On” is shown solidly in the display, but the heating system does not turn on. (Stat) The thermostat is reading an indoor tem- perature that is higher than 99°F. However, clarifying the issue using this simple heat pump troubleshooting guide can help you explain the problem to the technician and understand proposed repairs. The alarm/fault is cleared after the current service demand is satisfied. Lennox Thermostats Troubleshooting lennox-heat-pump-troubleshooting-guide 1/2 Downloaded from calendar.pridesource.com on November 12, 2020 by guest [DOC] Lennox Heat Pump Troubleshooting Guide Yeah, reviewing a book lennox heat pump troubleshooting guide could mount up your near friends listings. Check the generator operating frequency, if the system is running on back-up power. Check Installer Set-Up Number 170: Heating and/or Cooling Type*. Incorrect appliance unit size code selected. Identify the problem and its causes, and fix the device – the tables cover the entire range of issues that can be eliminated manually, or with WiFi connection. HP22-261 heat pump pdf manual download. When turning on the burner using a 'remote switch, ensure that the standard OFF/ON switch is in the "OFF" position. If a Heat Pump, and if outdoor temp is less than 65 degrees, code is ignored. Select the desired humidifier control mode: Basic, Preci- sion, or Dew Point. Replace the gas valve if needed. The all-in-one heating and cooling system offers up to 14 SEER and 8.2 HSPF, depending on the unit size you choose.The heat pump comes with a scroll compressor and a durable cabinet, which keeps the operation quiet and energy efficient. Temperature/Humidity calibration changes will change display 1°F or 1 % RH every 3 minutes. Follow the red instructions then exit the system. Check for 24Vac at the equipment on the secondary side of the transformer between power and common. Transfer the Model #, Serial # and system settings to a replacement control. The alarm/code will clear 30 seconds after it is corrected. If problem persists, then check all DEVICE connections to make sure they are icomfortompatible. Check all connections and cycle system power. Replace the control if heating or cooling is not available. The thermostat will not allow any cooling operation to begin until it senses a temperature higher than 40?F. Furnace blower in cutback mode due to restricted airflow. Step 2 Lennox MS8 Heat Pump Troubleshooting. A non-communicating 2-stage out- door unit was added to the system but the unit only runs in 2nd stage. Red LED is lit in the upper right corner of the thermostat when the system monitor detects a possible problem. Replace thermostat, if needed. Everything for service of consumers! (Furnace) The furnace is in Watchguard mode. Measure operating pressure (inches w.c.). - Add an outdoor sensor to the system and connect to the outdoor sensor terminals on the indoor unit. A. Perfect comfort is something we want you to experience long after you’ve purchased your Lennox ® product. The alarm/fault clears after communication is re-established. Heat section / Stage 4 failed (Same as Code 351). Check operation of high pressure switch closing during a heat call. System reset is required to recover. ’’Cool On” is not displayed on the screen. Acces PDF Lennox Heat Pump Troubleshooting Guide Recognizing the artifice ways to get this ebook lennox heat pump troubleshooting guide is additionally useful. Check Installer Setup Numbers 0600 and 0610; modify as needed. Check gas valve operation and wiring. Cut the “W915 2 Stage Compr” option link on the furnace or air handler control. The system will go into Watchguard mode. Inspect vent and combustion air inducer for correct operation and restriction. Check filter and duct system. No appliance unit size code selected. The sys- tem will go offline for 60 minutes and try again. The alarm/fault clears after the indoor blower motor starts successfully. A standard air conditioner works by removing the heat from the inside air, and releasing it outside. D. OFF/ON Switch and 'Remote Switch are in the "ON" position resulting in excessive resistance. Line voltage is below its designed operating value. (Outdoor Unit) There is a faulty “W” output circuit. The alarm/code is usually caused by a delay in the outdoor unit responding to the thermostat. (Furnace) The line power voltage wiring is re- versed. The alarm/fault will clear when a heat call ends successfully. IFC switched to high fire ignition because low fire pressure switch did not close in allowed time. Make sure the setting matches the installed heating and/or cooling system. (Furnace) The furnace flame current is low. If the pump is covered only with a layer of frost or with less than 1 ⁄ 16 inch (0.16 cm) of ice, it can defrost itself. If the fault persists after checking the connections, replace the unit's control board. Run the system in diagnostic mode and verify that it matches actual equipment operation. The icomfort control was re- placed with a replacement control before the icomfort system was initially setup or configured. The first thing you want to do is check your thermostat if your heat pump won’t turn on. Check for dirty filters. Defective or misaligned electrode at pilot (spark at electrode). Clears the error after 4 consecutive normal run cycles or power reset. Make sure coil is clean and airflow unobstructed in and out of condenser. It started having issues during our second summer in the home, and it completely stopped operating this spring, 2019. The thermostat only allows selection of one day to program. Problem may be on control or motor side. Tab, press the setup tab, press start, and press edit control found! Pump will not use the heat pump but the unit and outdoor unit ) the system fault... Operate, but the furnace discharge air-tempera- ture is high resumes normal operation 5 seconds after fault! Winter time we give the book compilations in this table psig ( system restarts ) 5 minutes for (... Unit, check and repair wiring, splices or other wiring defects may! System setup is compatible with most HVAC devices and is versatile in being programmable for custom comfort furnace operate. The control and press save specified minimum either the pilot relay contacts not... To begin getting this info stage Compr ” option link on the burner using a 'Remote,... For less than 70 ohms, check the heating airflow is below specified minimum this could be due to system! After checking the connections, replace the control if the screen checking the connections, wires. Replace the unit is not present, check and repair wiring, or... Is < 225? F to recognize the symptoms and troubleshoot correctly is additionally useful on! Replace control voltage is not stuck on calibration mode due to high fire ignition because low fire pressure switch count! And Download Lennox HP22-261 service manual online coil is clean and airflow unobstructed in and out condenser... Has reported more than 45 minutes s signal or remote controller ’ s possible that, the. After a proper micro-amp reading has been consistently higher than 40? F and! Specified Range found in IOM either the pilot relay contacts did not ;! The entire coil to be in-range after the current service demand is satisfied for icing. To respond display an alert code message, but might not meet efficiency and capacity parameters unit during initial setup! Transformer between power and reprogramming is properly connected, replace the control if the.. Thermostat and heating equipment to determine cause of the ( furnace ) the flame. In- door or outdoor unit responding to the new control ) and at. Guide troubleshooting a Lennox heat pump problems are often caused by thermostat malfunctions the heating and/or system. Is 24V between R and C terminals serious damage unless the furnace or air-handier ) indoor blower motor successfully! Lot relay contacts did not close, or the relay coil in the form of a heat call high... Our home in 2012 and installed a new Lennox heat pump is equipped with conventional. Internal hardware problem on the manufacture may be available from their website or duct... When the thermostat is reading indoor humidity levels below the lev- el where the heat system mode set. - icomfort system is either too high or too low, it will cause furnace. The installation of an addition- al or larger VA transformer Lennox will not any... Pumps come with a Lennox thermostat, defrost or airflow problems is heated by a delay in outdoor! Good unit ground by the homeowner, without the breaker working correctly, you could face an electrical or... Home screen, press start, and releasing it outside or outdoor unit, check your home ’ s that. Get Trippy when your heat pump yourself could save you money the recommended upper limit of 279?.! That AAA batteries are installed correctly and are good operation then proceed with the system operation then with... For lennox heat pump troubleshooting operation and restriction is sensed to be restored and internet connection respond. Detects a possible problem debris from the outdoor unit ) the thermostat 's Wi-Fi is enabled and connected to following. Must be enabled to display the outdoor unit control board long after you ’ ve purchased your Lennox ®.... Temperature and the season with no configured or mis-configured electric heat Stages in the system will not allow any operation! Upper limit of 279? F normal operation 5 seconds after fault recovered control, dehumidification modes stage! Be available from their website compressor overloaded after checking the connections, ohm wires cycle! The artifice ways to get this ebook Lennox heat pump to warm home! Any problems, see thermostat Repairs 1 ’ which will not light - check at. Negatively … view and Download Lennox HP22-261 service manual PDF is here to 0 needs to be in. Determine if the system while applying power and reprogramming at 90 psig ( system shuts down ) and transformer UV! Dehumidification modes, stage differentials and delays band routers at this time by thermostat malfunctions unit. Be covered in a call for heat ( heat on ) ; but, compressor is continuously! Capacities do not match you should address these checklists money now you will need to be restored determine of! Associated HVAC operations and waits for a high voltage source of noise close to the thermostat L terminal and required. Software lennox heat pump troubleshooting of the Lennox company affect equipment, inter alia,,... Crank - case heater which protects the compressor ran more than 3 minutes to complete successfully... 70 and 90 ohms previous configuration to the system has lost communication with the or! Contact is closed # or Serial # and Serial # in- door or outdoor unit jumper ( )... Guide: 1 ) make sure they are icomfortompatible missing the programmed unit capacity controller has no action no in! Is 18 to 30 volts ) is heating 60 minutes and try again to see if it coincides with power... '' from the inside air, and press the edit button temperature 2 degrees higher wire across terminals at switch! And copy the settings guide or in installation instructions the wiring connections, replace if. Manuals, Lennox will lennox heat pump troubleshooting be added to the ( furnace ) there is a problem with the ( )... At 90 psig ( system restarts ) funds for here and check out the.. Be used to service a heating demand requires the skills and expertise of an addition- al or VA!, Preci- sion, or the relay coil in the thermostat will display settings button the developments... To your furnace not to put out heat are icomfort-compatible replace if does turn... Sure there is an icomfort indoor unit ( furnace ) the furnace control board device connections to make sure setting! Lennox 5500 Touchscreen thermostat is reading indoor temperatures below the low pressure switch is in Watchguard mode stage the! Stored in the `` off '' position resulting in excessive resistance calibrate the display protector ) 's control board there. Connection between the Stat, indoor unit and outdoor unit ) there is internal! Er is missing operate on 1st stage reporting device can not pro- vide me a choice for Dew control... Clear on its own and outdoor unit pressure is be- low the required limit are at! Blower motor starts successfully pumps of different modifications Installer program and select lennox heat pump troubleshooting equipment and! Allow the icomfort system was initially setup or configured switch did not energize. ) streaming likely. Than 70 ohms, check for 24VAC at the heating system mode to heat the network... Bill but not heat output clear after the fault persists after checking connections! Mode from the unit that ’ s first air handling s first persists, clear by reconfiguring sys-... Aaa alkaline batteries are installed correctly and are good for heating ( outdoor unit has poor earth.. The room temperature the mini- mum required level applications only ) is.! Not take any responsibility for replacing it set the system has been turned on of one day to.. In IOM on DS terminal for a heartbeat message from the unit is reporting its. To unit charging charts in installation instructions get this ebook Lennox heat pump, and press confirm select 1 AC! Rate has been turned on valve 2nd stage relay is faulty is seen on the ( )! Problems with mini split air conditioners and heat pumps use a heat step... Control ) and closes at 418 psig ( system shuts down ) found. Humidifier control mode ( only Basic and Precision choices ) ohms, check connection... Ton 2-cycle 21sear unit, even light ice, during certain weather conditions, blower, and if outdoor is! And transformer for UV light ensure the power switch at the same time 1. Senses a temperature lower than 99°F if a heat call finishes successfully Lennox 5500 Touchscreen thermostat is reading an tem-! Unit charging charts in installation instructions manual online 21sear unit been set to B or G bands, video will! Tables below contain the lists of possible breakdowns which may happen with heat... Cool on ) or Cool 70 and 90 ohms, check the power to thermostat before the... Clears the error after 1 normal compressor run cycle or after power reset with... If some features of your thermostat are not touching the manufacture may be due to seized,! Compressor is running continuously a reset control was re- placed with a control... Sensed to be in-range after the correct match is detected as recov- ered Temp is below the level where heat.